It has been the vision and mission of Excel Comfort Services to proivde Forest Park, OK with the highest quality of service for heating, cooling, plumbing and everything else we provide.
Find out how we meet this goal with each and every heating, cooling and plumbing job in Forest Park, OK by taking a look at our reviews.
for Forest Park, OK
Our Reviews by City
Ms Ghita - Forest Park, OK
Response from Excel Comfort Services:
THANK YOU GHITA!!! It is always a pleasure to work for such lovely clients as yourself. WE HAVE THE BEST CLIENTS EVER!!!
North ac Condensing unit 44.3/5.95 mfd capacitor rated@45/5 mfd 246.6 volts ac Compressor rla 9 amps O.d. condenser fan motor rla .7 amps R410a refrigerant txv metering device Low side suction pressure 121 psi 14 degree superheat 259 psi high side liquid line 2 degrees superheat South ac Condenser system 69.4/14.42 mfd capacitor rated @70/15 246.3 volts ac 11.1 amps rla compressor 1.4 amps rla o.d. fan motor R410a refrigerant txv metering device Low side 130 psi 15 degree superheat
Home owner is ready to have air ducts cleaned chose premium-level service for cleaning air ducts
Gas fireplace repair near Oklahoma City Zoo
Doing gas furnace tune-up maintenance agreement service and also doing gas fireplace maintenance service client said she called Local Company and we were able to get out the same day to service gas furnace by Trane also has an Armstrong air gas furnace 80% afue rating installed last year by a different local HVAC company
Finding short in electrical wiring of 230-volt single phase 12 gauge wiring going to Plumbing well pump motor and controls including pressure switch and hard start kit capacitor near Remington Park near National Cowboy & Western Heritage doing plumbing repairs now for plumbing maintenance service agreement customer
Installing new high-efficiency gas furnace 80% afue rated was currently in there right now and replacing that gas furnace with new 96 + percent gas furnace variable speed fan motor
A.c. not cooling home near twin hills golf & country club doing a.c. repair on dirty clogged condensing unit coil client thrilled to have a.c.
Installing new Goodman evaporator coil near Remington park